Floatless Switch, Compact Plug-In Type61 F-GP-N 61F-GP-N AC200
- 61F-GP-N AC200
- Package Qty.
- Ship pack of
- Withstand Voltage
- AC2000V 50/60Hz 1min
- Rated Voltage (V)
- AC200(50/60Hz common use)
- Tolerable Voltage Fluctuation
- Rated voltage of 85 to 110%
- Ambient Humidity
- 45 - 85%RH
- Weight (g)
- About 155
- Pin Type
- 11 pin
- Reset Resistance between Electrodes (ohm)(Recommended Value)
- About 15 to infinity
- Response Time
- During operation: 80 ms or less
During reset: 160ms or less
- Cable Length (m)
- Below 1k
(600V0.75mm2when using 3-core completely insulated cabtire cable)
- Controlled Object, Using Condition
- Common clean water, waste water
- Electrical: 100,000 times or more
Mechanical: 5 million times or more
- Current between Electrodes
- AC about 1 mA or less
- Voltage between Electrodes
- Outside Dimension (mm)
- Height 49.4x width 38x depth 84
- For general use
- Operating Ambient Temperature (deg C)
- -10 - 55
- Insulation Resistance (Mohm)
- 100 or more (for DC500V meggers)
- This product is manufactured in Japanese standards. Please check the specification before you order., Insulation resistance and electric strength are the value between power terminal and terminal electrodes, between power terminal and terminal, and between contacts between terminals.
- Dynamic Resistance between Electrodes (ohm)(Recommended Value)
- 0 to about 4k
- AC250V 3A (resistance load)
AC250V 1A (inductive load cosphi =0.4)
- CE standard conformity
UL/CSA standard certified product
- With LED operation indicator Output ensures independent 2c connection
Customers Who Viewed This Item Also Viewed
| 5 star
| 4 star
| 3 star
| 2 star
| 1 star
6 Customer Reviews
The reviews are automatic translation.
It is for exchange.
On 2017-03-29 18:03:53
Correspondence, goods, is satisfied with the packing both. Also I will try to buy.
On 2016-05-16 09:07:12
Start and stop for the water level electrode of automatic operation
On 2015-03-10 18:21:14
Early until the arrival from the order, have survived can be used with confidence because manufacturers goods.
Replacement of mechanical parts
On 2014-07-14 20:09:03
In particular, you can use without any problems. Cheaply from the manufacturer, we want to use if it so early also accommodate other parts.
We are using the water level of the raw water tank factory.
On 2013-12-18 17:12:50
We used without problem that was exchanged for a number of years deterioration.
As the control panel of the parts of the pump, use
On 2013-07-24 16:49:02
A control panel of the parts of agricultural water, malfunction occurs when subjected to lightning or the like. To be able to 100V200V-service, thankfully. Since the existing control panel of the parts replacement, so, is intended to break, no, but as spare parts, including, I bought.
Customers Who Bought This Item Also Bought