Super Timer ST7P Series ST7P-2 AC200V 60M
ST7P-2 AC200V 60M
Ship pack of
This product is manufactured in Japanese standards. Please check the specification before you order.
Tolerable Voltage Fluctuation
85 to 110%Vn
Insulation Resistance (Mohm)
More than 100 (at 500V Mega)
Minimum Adaptable Load
DC5V, 1mA (reference value)
Allowable Around Temperature (degree c)
-10 to +50(No freezing No condensation)
1 min (operation circuit between the control output) AC1000V 1 minute (non-charging metal part between the charging unit) AC1500V 1 minute AC2000V (non-continuous contact portions between)
Impact Resistance (Malfunction)
50m / s
2 sup> (up, down, left and right, each twice the three-axis direction of the front and rear) Recovery Time
(I return including middle) 0.1 seconds or less
(Up, down, left and right, each 1 hour 3-axis direction of the front and rear) 10 to 55Hz double amplitude 0.75mm
Time Limit Contact
Rated Voltage (V)
AC200 to 230 (50/60Hz)
Allowable Relative Humidity (%)
(Icing, no condensation) 35-85
3A AC240V (resistive load)
4 to 60min
(1800 times / hour AC220V 3A resistance switching frequency) 500 000 times or more
(1800 times / hour no-load switching frequency) 50 million times or more
Vibration Resistance (malfunction)
(Up, down, left and right, each for 10 minutes three axial directions of the front and rear) 10 to 55Hz double amplitude 0.5mm
1000m / s
2 sup> (up, down, left and right, each five times three axial directions before and after)
Customers Who Viewed This Item Also Viewed
5 Customer Reviews
The reviews are automatic translation.
On 2015-07-06 11:55:20
There is no problem especially about the product.
Used in combination with relays as delay stop circuit of blower motor of equipment of hobby
On 2015-04-25 17:44:07
Incorporating an off-delay circuit in combination with a relay, it is extremely compact and the time setting is also almost accurate and perfect.
Vinyl house control system
On 2014-10-31 17:29:58
I organize various control systems myself but I am satisfied with the size and price. Strongly speaking, the number of the scale is small and it is hard to see.
To the facility timer
On 2014-09-22 00:27:06
It is a good product.
Create control circuit
On 2013-03-07 14:10:05
I think that it depends on the circuit to use, but I am using it because it has better performance than Omron.
Customers Who Bought This Item Also Bought